Burger King Lighting Retrofit Case Study
Independence LED retrofitted the lighting at a Burger King in Carteret, NJ, and published a case study showing the business model of the retrofit.
Like many similar Burger Kings that are about 2,400 square feet in size, this location has 35 troffer fixtures that are 2’x4’ with four 32-watt fluorescent tubes, totaling 128 watts per fixture. At 8,760h/year the fixtures each used 1,121 kWh/year. With an electricity rate of $.083/kWh, the lighting cost was $93 per fixture per year and $3,257 for all 35 fixtures.
By reducing the fixture wattage from 128 to 44, using a 44-watt LED Retrofit Kit, the annual savings is 735 kWh and $61 per fixture. With 35 fixtures, the annual savings is $2,137. This franchise owner has 46 locations.
- Existing Building Technologies Combine for Increased Savings
- Top 3 Reasons to Calculate Your Environmental Footprint
- How to Use Lean Tools to Cash In On Environmental and Energy Savings
- Sustainability Reporting for Commercial Real Estate: GRESB
- Six Essential Steps to Drive Effective Energy Management
- Integrated Building Optimization
- Mobility From The Plant Floor To The Store Door: Improve Safety, Accuracy, and Productivity
- Alarms Management: The Future is Now
- 4 Reasons Operations Teams Can’t Live Without Real-Time Building Data
- 2013-20114 Winter Polar Vortex
- Cut Costs and Improve Facility Operations with Energy Data
- Energy Procurement Strategies for Winter 2014 and 2015
- Energy Efficiency Requires Engineering Efficiency
- Integrated Building Optimization: A Crucial Convergence of Demand-side and Supply-Side Energy Management Strategies
- Driving Productivity and Profit with Industrial Energy Management