Housing Corp. Switches From Fuel Oil to Natural Gas, Saves $2.8m
Climate Change & Environmental Services (CCES) managed the construction management and environmental permitting for a major boiler modernization project for a large apartment complex in New York City that has reduced emissions and saved the complex over $2.8 million in fuel costs compared to the previous 12-month period.
East River Housing (ERH) Corporation operates a boiler house providing heat and hot water to a number of apartment buildings with over 2,700 units plus a shopping center. It had been combusting over 2 million gallons of No. 6 fuel oil annually. The housing corporation decided to modernize the boilers and switch from fuel oil to natural gas.
ERH replaced one aging boiler with a new modern unit and renovated its other two existing boilers, installing new low NOx burners with flue gas recirculation. ERH worked with Con Edison, the local utility, to bring a natural gas line into the boiler house for the fuel switch.
No. 2 diesel oil is to be used as a backup during natural gas interruptions, necessitating the installation of a new tank farm replacing the No. 6 fuel oil tank farm.
CCES carried out construction management to address scheduling and technical issues with the implementation of the installation and testing, as well as all environmental permitting. The physical installations are complete and the plant has operated under natural gas for one full year now.
CCES has assessed the cost savings due to the project. Given natural gas being piped to the facility, removal of No. 6 oil tanks, and use of a modern No. 2 oil tank farm, ERH virtually eliminated the risk of a messy oil spill in the densely populated area. In addition, emissions of pollutants critical in an urban area all markedly dropped because of this project, such as NOx (85%), particulate matter (75%), greenhouse gases (equivalent of removing 4,600 cars from the road), and SO2 (99%). These reductions helped change the permitting status of ERH from major to minor, saving them much in fees and removing several regulatory requirements.
CCES determined that themal efficiency improved by about 18% (fewer therms to create steam). “We are not sure if the thermal efficiency improved because of natural gas being more fluid than No. 6 fuel oil, which is thick and viscous or because of the new equipment. But probably both contributed,” said Marc Karell, principal with CCES.
CCES also calculated cost savings. In the 12 months of natural gas service (May 2012 through April 2013), ERH directly saved over $2.8 million (63%) in fuel costs compared to the previous 12-month period, despite this being a measurably colder winter than the one before. CCES also calculated avoided cost savings (added fuel costs ERH would have had to incur if ERH still combusted No. 6 fuel oil with the old boilers). The avoided cost savings for the 12-month period was conservatively estimated to be over $5.3 million.
The project payback, initially anticipated to be about 4 years, will be under 2.5 years based on direct cost savings.
Asked if switching from fuel oil to natural gas was a viable option for other facilities, Karell said it depends on the availability of natural gas and the cost of extending a natural gas line to the site.
- Combined Heat and Power
- 2015 Environmental Leader Product & Project Awards
- Gartner Magic Quadrant
- Case Study: Dassault Falcon Jet Taps Intelligent LED Lighting Solutions
- 2015 Insider Knowledge
- Improve Your Company's Environment and Energy Performance
- NAEM Research Report: Planning for a Sustainable Future
- How to Thrive in Today's EHS Landscape
- Verdantix Green Quadrant for EHS Software
- Migration to Mobile: The Evolution of EHS Management Tools