Russelectric Upgrades Hospital’s Emergency Power System
With enough capacity to power the 660-bed hospital, as well as a planned seven-story heart center and the eventual addition of a cancer center, the new system was designed to meet the needs of the hospital now and well into the future.
The upgrade included replacing three 1.25 MW generators with two new Caterpillar 3 MW generators (one 2.25 MW Caterpillar generator was retained). An automatic transfer switch and uninterruptible power system were also added.
The system’s two 40,000-gallon fuel tanks, if full, would allow the hospital to meet its peak demand of about 5,200 kW for nearly six days. The substation was replaced with four utility-owned parallel transformers with a total utility capacity of 10,000 kVa. If one utility transformer goes down, the hospital will still be able to maintain uninterrupted service, even at peak demand, since the other transformer has a capacity of 7,500 kVa. Should both transformers go down, the hospital’s generators will kick in until the utility source is restored.
Switches and switchgear were relocated from the main hospital building to a new central energy plant, so there is plenty of room for more switchgear and circuit breakers, if needed, the Mission Critical article said.
If there is an unusually high demand for power, the system allows the hospital to quickly curtail its load should the utility ask it to do so. As a result, the hospital receives contractual rebates, which allows it to reduce its overall energy costs.
The new system also features a supervisory control and data acquisition (SCADA) system, which was brought online in early 2013. The SCADA system provides interactive monitoring, real-time and historical trending, distributed networking, alarm management, and reporting for all aspects of the power system. If there is an internal failure, the SCADA system will automatically bypass the failure and re-energize the system without starting the generators. It also has a full manual backup.
The installation and switchover of Rex Hospital’s emergency backup power system was completed with a single, planned 10-second outage.
Photo credit: Photograph of Rex Hospital via Rex Healthcare.
- Integrated Building Optimization
- Guide to Energy, Carbon and Environmental Software
- Trends in Energy Management: Where Should Your Next Investment Be?
- 2014 Environmental Leader Product and Project Awards
- Essential Guide to Lighting Retrofits and Upgrades
- How "Fixed" is the Fixed Price Product?
- The CFO and the Sustainability Reporting Chain
- NAEM Research Report: Planning for a Sustainable Future
- Sustainability Careers: Unlocking Hidden Employment Potential
- Alarms Management: The Future is Now
- Energy Efficiency Requires Engineering Efficiency
- Integrated Building Optimization: A Crucial Convergence of Demand-side and Supply-Side Energy Management Strategies
- Driving Productivity and Profit with Industrial Energy Management
- Energy Procurement in 2014: Products & Programs to Optimize Savings
- BUYING STRATEGIES IN A VOLATILE MARKET: What Businesses Need to Know about Retail Electricity Procurement